It appears the acromag1 box was reset again. This might have to do with the flooding in the adjacent ATF lab stopping power there.
I have ordered the APC SMX3000LVNC UPS unit. The UPS tracking says it arrived Wednesday last week. My defults for TechMart punchout were missing the LIGO mail code so stuff is taking a bit longer to get to me through the internal mail system. Should be here this week.
Power budget for essentials.
70 W (100 W max)
740 W (990 W max)
APC SMX3000LVNC unit: battery capaciy 738 Volt-Amp-Hour
At the upper bound of consumption (at start of unit life) this will ride out 45 min blackout.