Not logged in
Fri Sep 5 09:56:14 2008
Funny channels, reboots, and ethernet connections
1) Apparently the I00-ICS type channels had gotten into a funny state last night, where they were showing just noise, exactly when Rana changed the accelerometer gains and did major reboots. A power cycle of the c1ioo crate and appropriate restarts fixed this.
2) c1asc looks like it was down all night. When I walked out to look at the terminal, it claimed to be unable to read the input file from the command line I had entered the previous night ( < /cvs/cds/caltech/target/c1asc/startup.cmd). In addition we were unable to telnet in, suggesting an ethernet breakdown and inability to mount the appropriate files. So we have temporarily run a new cat6 cable from the c1asc board to the ITMX prosafe switch (since there's a nice knee high cable tray right there). One last power cycle and we were able to telnet in and get it running.