I've completed bench testing of all seven vacuum Acromags installed in a custom rackmount chassis. The system contains five XT1111 modules (sinking digital I/O) used for readbacks of the state of the valves, TP1, CP1, and the RPs. It also contains two XT1121 modules (sourcing digital I/O) used to pass 24V DC control signals to the AC relays actuating the valves and RPs. The list of Acromag channel assignments is attached.
I tested each input channel using a manual flip-switch wired between signal pin and return, verifying the EPICS channel readout to change appropriately when the switch is flipped open vs. closed. I tested each output channel using a voltmeter placed between signal pin and return, toggling the EPICS channel on/off state and verifying the output voltage to change appropriately. These tests confirm the Acromag units all work, and that all the EPICS channels are correctly addressed.