you asked for: diff 2008/09/25,0:00 2008/09/25,8:50:19 utc 'FSS[-_]SLOW'
LIGO controls: differences, 2008 09/25 00:00:00 utc vs. 2008 09/25 08:50:19 utc
__Epics_Channel_Name______ __Description__________ __value1____ __value2____
C1:PSL-FSS_SLOWKD 0.000000 0.001000
C1:PSL-FSS_SLOWKI -0.001000 -0.001700
C1:PSL-FSS_SLOWKP -0.000300 -0.001000
netgpibdata.py -i 188.8.131.52 -d AG4395A -a 10 -f spectrum01
Last login: Fri Sep 19 00:11:44 2008 from gwave-69.ligo.c
Sun Microsystems Inc. SunOS 5.9 Generic May 2002
svn: This client is too old to work with working copy '.'; please get a newer Subversion client
SunOS nodus 5.9 Generic_118558-39 sun4u sparc SUNW,A70 Solaris
- setsval.m uses mDV to get the minute trend from some specified start time
and duration in the past. It then writes that 'good' value to the
.SVAL field of the SUSPOS, SUSPIT, and SUSYAW records for all the
- setHILO.m reads the .SVAL field and then sets the alarm levels and severity
for the same records given a "sigma" as an argument. i.e. 1 sigma = HIGH,
2 sigma = HIHI.
scp Particle.st firstname.lastname@example.org:/cvs/cds/lho/target/t0sandbox0
scp Particle.o email@example.com:/cvs/cds/caltech/target/c1psl/
At the request of Steve, I modified the HIGH value of C1:PSL-FSS_RMTEMP from 21.27 to 23.0.
The HIHI is set to 23.50.
Since we reduced the integration time of the particle counter by a factor of 10, we had to add a gain of 10
to the EPICS channels C1:PEM-count_full and C1:PEM-count_half.
I asked Alex to change it and he did it. I forgot to ask him to change the gain of C1:PEM-count_half. So now only
C1:PEM-count_full has x10 gain.
C1:PEM-count_full and C1:PEM-count_half are 'Soft Channel' records in the database (Pcount.db). The values are actually
written into the VAL fields directly by an SNL code Particle.o.
Particle.o reads data from the RS-232C port, to which the particle counter is connected. Then it parses the data and put values
into relevant EPICS channels using channel access. This means we cannot change the gain of the channels by modifying the
database file. For example, ASLO field does not have any effect when the value is directly written into the VAL field.
We had to modify the SNL code. Alex modified Particle.st and the new SNL object file is Particle_x10.o sitting in
/cvs/cds/caltech/target/c1psl/. I modified seq.load so that c1psl loads Particle_x10.o when rebooted.
The source code for the old Particle.st can be found on lesath.ligo.caltech.edu in
I asked Alex to disclose the location of the source of the new code.
In order to compile the SNL code into an object file for Motorola CPU by ourselves, we have to call Dave Barker at LHO.