I removed POX rfpd to see how it is mounted on its base. It is here on the work bench just in case someone wants to use it the IFO over the week end.
I put POX back to it's place with markers. The pd was removed from it's base so it is for sure misaligned.
I was told yesterday, that on Friday the construction people accidentally ripped out one of the 40m soil ground.....AND HOW MANY MORE ARE THERE? nobody knows.
It was ~8 ft long and 0.5" diameter buried in the ground. There is no drawing found to identify this exact building ground. They promised to replace this on Wednesday with a 10 ft long and 0.75" diameter.
The the wall will be resealed where the conduit enters the north west corner of the IFO room 104
There should be no concern about safety because the 40m building main ground is connected to the CES Mezzanine step-down transformer.
Atm1 is showing ground bus under N-breaker panel in 40m IFO room north-west corner.
The second ground bus is visible farther down south under M-breaker panel.
Atm2 is the new ground that will be connected to ground bus-N
The RGA isolation valve VM1 was closed since Aug 24, 2009 I installed the new UPS that time.
The last RGA scan in the log is from Aug 7, 2009 The vacuum rack UPS failed on Aug 15, 2009
I opened VM1 today so we can have ifo rga scan tomorrow.
You said that the use of FAXST was forbidden for phds and graduate students. I had to swear on the promise of not ever buying an other FAXST
FSS_RMTEMP is moving up and daily fluctuations are less . 120 and 16 days plots are below.
Rob found puddles of water very close to the chiller during lunch time. We raised the unit and took the side cover off. All surfaces were dry and the water level in the tub normal.
Later on we discovered that one of the Vons distilled water bottle was leaking. Jenne and I checked for excess amount of condensing water droplets inside the MOPA box.
On the bare,not insulated tubing and valve are loaded with droplets of water. Relative humidity is 44% at 24 C and HEPA filter speed set to 80 V in the enclosure.
Earthquake of magnitude 5.0 shakes ETMY loose.
MC2 lost it's damping later.
The EQ did not change the input beam pointing. All back to normal, except MC2 wachdogs tripped again.
Awesome 5 hrs of locking Rob!
Pointing stability of 4 days. Initial pointing does not go through suspended optics. It is launched right after the Piezo Jena steering mirrors in the BS chamber.
IP-ANG on epics screen is C1:ASC-IBQPD_X and Y in dataviewer were recentered. This beam is clipping a bit in ETMX chamber pick off mirror.
IP-POS pick off is in the BS chamber and it's qpd on the BS_ISCT This beam is also clipping just a little bit. This is easy to fix. We'll have to remove an iris from the BS optical levers table.
note: arms were not locked when I recentered
Kiwamu, Alex and Zach are practicing mandatory IR-safety scan at the 40m-PSL
40m specific safety indoctrination were completed.
Initial pointing beam is clearly clipping on 2" pick off mirror in ETMX vacuum chamber.
Atm. 1 The pick off mirror is just north west of the ETMX test mass
Atm. 2 The camera is looking in from the north view port of ETMX chamber. The back side of pick off mirror is visible now with the face view of the "IP-ANG-OUT" mirror.
IP-ANG clipping can be traced back to our last vent of Aug. 18, 2008 See elog entry #845
This was an after earth quake - sus repair vent
Pump down #66 is 435 days old. RGA scan is normal. New maglev is fine. New UPS is in place but not hooked up to communicate.
V1 has bare minimum interlock. Pirani vacuum gauges PTP1 and PRP do not communicate with readout system.
There is no emergency dial out in case of vacuum loss. Our existing vacuum dedicated desk top computer is dead.
New cold cathodes, Pirani gauges and gauge controller should be added.
In general: vacuum system needs an upgrade !
The laser power is down 5-6%
The PMC power is seems to be on the rise, ( MOPA_AMPMON is dropping ?) but I do not think it is real. We have Santa Anna wind condition, when the relative humidity drops and ......
There is an other funky think. The room temp became rock solid. The PSL HEPAs running at 20% and IFO-room ACs are also in normal operational mode.
Illuminators and PSL lights turned off.
HEPA filter speed increased from 20 to 100%
Here is the plots for the powers. MC TRANS is still rising.
What I noticed was that C1:PSL-FSS_PCDRIVE nolonger hit the yellow alert.
The mean reduced from 0.4 to 0.3. This is good, at least for now.
Koji did a nice job increasing light power with some joggling.
The RFMnetwork is down. MC2 sus damping restored.
The PSL enclosure HEPAs turned on at 30%
MC2 damping restored, MZ locked and the arms are flashing now.
RFAMPD_DCMON disappered on Nov 5, 2009
The concrete floor cutting has begun next door at CES
ATM1: Seismometers are saturating, suspensions are OK
Atm2 : activity next door, diesel Backhoe and diesel concrete cutter are running
Atm3: CES exhaust fans output is pick up by 40M-Annex-North AC unit intake. The 40m office room has some diesel smell...........see # 2377
I added ~500 cc of distilled water to the laser chiller yesterday.
8 days plot: Thurdsay, Friday, Sat and Sun without construction
This first plot shows the RC temperature channels' performance from 40 days ago, before we disabled the MINCO PID controller. Although RCTEMP is supposed to be the out of loop sensor, what we really care about is the cavity length and so I've plotted the SLOW. To get the SLOW on the same scale, I've multiplied the channel by 10 and then adjusted the offset to get it on the same scale.
The second plot shows a period after that where there is no temperature control of the can at all. Same gain scaling has been applied to SLOW as above, so that instead of the usual 1 GHz/V this plot shows it in 0.1 GHz/V.
The third plot shows it after the new PID was setup.
Summary: Even though the PID loop has more gain, the true limit to the daily fluctuations in the cavity temperature and the laser frequency are due to the in-loop sensors measuring the wrong thing. i.e. the out-of-loop temperature is too different from the in-loop sensor. This can possibly be cured with better foam and better placement of the temperature sensors. Its possible that we're now just limited by the temperature gradients on the can.
Here is a 7 years plot of of the 40m temperature variations.
I've changed the watchdog rampdown script so it brings the SUS watchdogs to 220, instead of the 150 it previously targeted. This is to make tripping less likely with the jackhammering going on next door. I've also turned off all the oplev damping.
Saturday's special event of braking up the large concrete pieces in CES bay was un event full.
Steve is summarizing the Video Matrix choices into this Wiki page:
Price: < 5k$
Control: RS-232 and Ethernet
Interface: BNC (Composite Video)
Please check into the page on Monday for a final list of choices and add comments to the wiki page.
Composite video matrix switchers with 32 BNC in and 32 BNC channels out are listed.
The construction activity is shaking the tables in the control room. The compactor- large remote controlled jackhammer is in the bottom of the 16-17 ft deep hole 15 ft east of ITMY in CES bay. The suspensions are holding OK. PRM, MC1 and MC3 are effected mostly.
Instead of doing RCG stuff, I went to Millikan to work on data analysis as I couldn't stand the fumes from the construction. (this morning, 8am)
Diesel fumes are pumped away from control room AC intakes with the help of newly installed reflector boxes on the CES wall fans.........see # 2272
The vacuum system is at 760 torr All chambers with doors on and their annuloses are pumped down.
PSL output shutter is still closed. We are fully prepared to star slow pump down tomorrow.
The plan is to reach 1 torr ~ in 6 hrs without a creating a sand storm.
Oplev positions before and after drag wiped arm TMs as of yesterday. Slow-mode pumpdown has started with 3/4 turn opened RV1 valve at 8am today.
Pump down is completed. Valve configuration is VACUUM NORMAL. CC1 pressure is in the ~8 e-5 torr PSL output shutter is opened.
We still had some ants visiting the sink area this morning. These ants seem to be addicted to our our Peet's coffe
Spectracide: Bug Stop insect killer was sprayed. Please wash your eating dishes well ! and keep area clean.
At ITMX, on the CES side, 5 Ft from the wall the jackhammer is on. The susses are holding well.
We have been waiting for this for 20 some years. Arrowhead water with cooler. AWESOME
I added 600 cc of Arrowhead Distilled Water to the chiller.
60 days plot shows that about every ~ 10 days I have to add some.
Please check the water level yourself.
We lost our key to the Lightwave 125/6-OPN-PS The key shop just made one look a like that works.
We are celebrating Rob's promotion to thesis poetry. These pictures were taken on December 9, 2009
Rob has finished all his measurements in the lab and is officially well prepared to graduate.
What was the power level, polarization and beam size at beam trap?
Rana noticed that recently the temperature inside the lab has been a little bit too high. That might be causing some 'unease' to the computers with the result of making them crash more often.
For the next hours I'll be paying attention to the temperature inside the lab to make sure that it doesn't go out of control and that the environment gets too cold.
Today the lab is perceptibly cooler.
The temperature around the corner is 73 F.
The 2W NPRO from Valera arrived today and I haf hidden it somewere in the 40m lab!
Rana was so kind to make this entry for me
CES construction is progressing. The 40m suspensions are bearing well.
atm1, PEM vs sus plots of 120 days
atm2, big pool walls are in place, ~10 ft east of south arm
atm3, 10 ft east of ITMY
atm4, ~60 ft east of ITMY
atm5, cold weather effect of N2 evaporator tower
The low PMC transmission alarm was on this morning. The PMC alignment needs a touch up.
The electrical shop has to connect the new power transformer at CES. This means we will have no AC power for ~8 hrs on Saturday, February 20
Is this date good for us to power down ALL equipment in the lab?
I have installed a slow start throttle valve in front of V3 This spring loaded valve will cut down on the flow at high pressures. There will be no more sand storme
and static built-up during pump down.
IN VACUUM beam heights are ALL 5.5" This is measured from the top of the optical table to the center of all TMs, mirrors and other optical components. This beam is ~36" above the floor.
PSL (inside of enclosure) main-output beam: PMC, MZ, RC and ISS are at 3" heights. IOO Angle & Position, MC-Trans and RFAM qpds are at 4"
ALL OTHER beam heights at atmosphere and different ISCT (interferrometer sensing, control optical table)s are at 4"
Joe and Alex are working on the computers. Our vacuum system is temporary "All off" condition: meaning all valves are closed, so there is no pumping. cc1 = 1.6e-6 Torr
Designated vacuum control lap top is trouble some to use. Joe finally fixed it and I switched valve configuration back to vacuum normal. Shutter is open