How can we improve the cleanliness of the 40m IFO room 104 ? May be Mario Batali crocs if you chief chef of the lab likes it. We can do more effective things.
Atm 1 is showing the lab air quality dependence on outside air measured at the top of the IOO chamber. This made me to measure the differential pressure between lab and out side.
Properly sized air conditioner is over pressurizing it's room by 0.05 [" Water] like clean assembly room.
The 40m at Vertex location is barely getting pressurized to 0.01 " W
The control room is OK with 0.04 " W but it's air quality is very bad! It is 10x worse at 0.5 micron than IFO room.
Every entry from well pressurized control room into barely pressurized IFO pumps dirty air to our "clean room."
This door should be closed.
The drill- room entry is ideal because it is using the same air conditioner as the main lab, therefore it has cleaner air.
Things to do: seal holes of CES walls, seal paint wall at south end so it will shed less, replace gas kits on doors.
I have plugged the cable tray space entering the control room above Rosalba.