Following the procedure in this elog, we effected a reset of the vacuum slow machines. Usually, I just turn the key on these crates to do a power cycle, but Steve pointed out that for the vacuum machines, we should only push the "reset" button.
While TP1 was spun down, we took the opportunity to replace the TP1 controller with a spare unit the company has sent us for use while our unit is sent to them for maintenance. The procedure was in principle simple (I only list the additional ones, for the various valve closures, see the slow machine reset procedure elog):
- Turn power off using switch on rear.
- Remove 4 connecting cables on the back.
- Switch controllers.
- Reconnect 4 cables on the back panel.
- Turn power back on using switch on rear.
However, we were foiled by a Philips screw on the DB37 connector labelled "MAG BRG", which had all its head worn out. We had to make a cut in this screw using a saw blade, and use a "-" screwdriver to get this troublesome screw out. Steve suspects this is a metric gauge screw, and will request the company to send us a new one, we will replace it when re-installing the maintaiend controller.
Attachments #1 and #2 show the Vacuum MEDM screen before and after the reboot respectively - evidently, the fields that were reading "NO COMM" now read numbers. Attachment #3 shows the main volume pressure during this work.
The problem will be revisited on Monday.