Current Acromag chassis status:
I found out that Acromag offers DIN rail mounting kits for the open boards, so we can actually fit both XT series and ES/EN series in the same boxes, depending on the signal needs. The primary design driver will be the ES footprint, but if we find we don't need that many channels in some of the units, it's interchangable. For the wiring to the front panel - for which we will have a standard front panel express design, but may order modified ones for the custom needs of the 40m, I will contract the same company that Rich used for the wiring in his DIO box (Panel mount connectors terminating in loose wires/pre-routed plugs for Acromag units). We will either run a single DIN rail along the length of the chassis, or have two in parallel across.
Lydia and I took close looks at the breakout arrangements on the rack sides, and determined that because of the many cross-connects between non-DAQ ports it is not possible to redo and debug this in a reasonable amount of time without essentially shutting down the interferometer. So instead, we will connect the chassis directly to the slots that were previously leading to the slow machines. They come in two different flavors: The ADC modules have 64 pins, while the DIO and DAC ones have 50. There are a couple things we can do:
Based on Rich's design I will get started on a parts list and wiring diagrams to send out to the cable company.